At Tricel, our tanks can be assembled to accommodate a wide range of capacity requirements ranging from 1000 litres to over 4 million litres of water storage. Internal partitions and ancillary items available on request speak with our sales team today to discuss your water storage requirements.
Guidelines for different model tanks
HEAVY DUTY COVER
Suitable for indoor and outdoor use, and for the storage of foul water. These tanks have internally flanged lid panels, similar to those used in the base.
HEAVY DUTY COVER AND FINISHED TO FORMAT 30
Suitable for indoor, outdoor use and for the storage of potable (drinking) water.
TYPES OF BOLTS
Standard tanks come complete with bolts galvanised to BS EN ISO 1464:1999, we recommend that consultants specify Stainless Steel grade 316 S16 bolts under water and on lid.
In any situation where there is only one water storage tank in a building and the capacity is greater than 1000 litres (220 gallons), BS EN 806 states “To avoid interruption of the water supply when carrying out repairs or maintenance, the cistern shall be provided with compartments or standby cistern”. Where drinking water is being stored, two separate tanks are recommended as it is difficult to detect cross contamination from one side of a division wall to another.
These should be used in any instance where condensation drips from pipework, or from the tank could cause nuisance damage or render floors wet and slippery.
BALL VALVE HOUSING
Enclosed chamber containing an access hatch above the level of the cover, permitting the level control mechanism to be mounted at a higher level than would otherwise be possible. The overflow(s) must be placed on the tank side wall and not on the Ball Valve Housing. Water must be kept below tank roof level. This is only necessary where very large ball valves are used.
Where tank depth is 1m or greater, internal and external ladders should be specified. If the tank is on a raised platform then ladders may be required on tanks lower than this height. Where the tank is 2m or more from the top of the tank to the finished floor level external ladders should be fitted with safety cages and comply to BS 4211:2005+A1:2008. Guiderail: A guiderail should be fitted enclosing all access points to the tank roof, where a tank is 2m or more from the top of the tank to the finished ground level. Additional safety guards may be required for ladders depending on their location. A risk assessment should be carried out by the end users to determine if this is required.
REVERSE BASE TANKS
(Externally flanged base) These types of tanks allow the tank to be totally drained down, as the base is flat, they also allow access to all the bolts from outside the tank. 600 mm clearance is required underneath the tank for access to the base bolts.
* The client shall ensure that potable water is not stored in tank compartments that are adjacent to compartments storing foul water due to the risk of contamination.
Extensive industry experience, manufacturing since 1973.
Tricel manufacture deliver & install cold water storage tanks across a wide range of industry sectors throughout Ireland & the UK. Tricel also provide import/export services for our international clients. Tricel has been Manufacturing water tanks since 1973, and are made from Glass Reinforced Plastics (GRP). This top quality material offers outstanding capabilities including long life, durability and is a cost-effective solution for water storage even in the harshest environments. Cold water storage is available for both potable and non-potable applications.
GRP Water Storage Tank Installations
Airports & Hotels