Guidelines for Installing Water Storage Tanks
The following recommendations are generally for elevated tanks, as tanks at elevated positions can cause serious damage to the surrounding area in the event of wall, pipe or structural support failure resulting in water spilling out at a fast rate.
Consideration must be given to minimise the effects of such an occurrence, in terms of the positioning of the tank and regular inspection for defects.
General Water Tank Installation
• Water tanks should be located so as to prevent water damage or consequential loss in the event of leakage occurring.
• All tanks which are located above water sensitive areas should have a bund wall around them with adequate evacuation ducts.
• All other tanks should have Condensation or Drip trays to prevent nuisance damage and to keep floors dry.
Over the years we have seen tanks fail due to age, lack of maintenance, failure of the structural supports underneath the tanks, contaminated water attacking the internal fittings, ball valve failure where overflows were not fitted, vandalism etc.
Water Tanks Installations on Elevated Structures
For water tanks located on top of elevated structures, a walkway of at least 1 meter should be provided all around the water tank to allow for maintenance and inspection. This walkway should comply with health and safety regulations.
Water Tank Installation on Top of Buildings
Water tanks located on top of any building should be sited at least 1.2 meters away from the edge of the building. It would be preferable if the water tank was sited 1.5 times the height of the tank away from the edge of the building. In the event of failure, this would allow the water to spread itself over a much wider area before spilling over the edge of the building and possibly taking personnel or debris with it.
Potable Water Tanks
To comply with the Health & Safety Executive regulations on the Control of Legionellosis 1998, Cold Water Storage Tanks must be located in areas that are “readily accessible for cleaning”. Regular Maintenance and Inspections as required by Health & Safety Legislation.
Wide range of sizes
Our tank capacity range from 45 litres to 4,546 litres
Custom One Piece Tank Options
Virtually Zero Maintenance Required
Rooftop Water Tank Installation – Handrails Health & Safety Requirements
Handrails may be necessary to satisfy Health & Safety Regulations. The type of railing required is dependant on the tank height, distance from ground level, access etc. Please confirm which handrail arrangement is required so that we can make the necessary inclusion. We can supply and install ladders and railings, but we must be informed of the exact details prior to quoting the project. We assume that the end user is making his own arrangements unless we are informed otherwise.
Extensive industry experience, manufacturing since 1973.
Tricel manufacture deliver & install cold water storage tanks across a wide range of industry sectors throughout Ireland & the UK. Tricel also provide import/export services for our international clients. Tricel has been Manufacturing water tanks since 1973, and are made from Glass Reinforced Plastics (GRP). This top quality material offers outstanding capabilities including long life, durability and is a cost-effective solution for water storage even in the harshest environments. Cold water storage is available for both potable and non-potable applications.
GRP Water Storage Tank Installations
Airports & Hotels